|Conventional Circuit Breaker, Circuit-Breaker Failure Protection, Overcurrent Protection, OVP(Overvoltage Protection), RCCB
|ISO9001-2000, CE, CCC
|Rated Peak Withstand Current
|Rated Operation Sequence
|Rated Current of Over Current Release
|Current Transformer Ratio
|4s Rated Short Time Withstand Current
|Rated Short Circuit Breaking Current
|Rated Short Circuit Making Current
|Rated Insulation Level
|Wooden Box Shipping
Floor-type boundary switch integrated prepaid metering device is a product that changes the high-voltage metering, switch, and control box on the column into a cabinet-type structure. Combination, the box is made of stainless steel or iron plate spray material. This product is easy to install in structure, beautiful in appearance, the high-voltage part is completely isolated from the low-voltage meter room, and the high-voltage room cannot be opened when the equipment is powered on. The product occupies a small area and is a perfect combination product for living areas, industrial and mining enterprises and box-type transformers. Personnel can directly open the door to view the bottom of the watch and operate the switch on the spot. The transformer is vacuum cast with fully enclosed epoxy resin, thus eliminating the problem of aging. The demarcation switch part adopts vacuum switch with zero-sequence and protection current transformers, and realizes zero-sequence, over-current and quick-break protection with intelligent controller, which can realize automatic removal of single-phase ground fault and automatic isolation of phase-to-phase short-circuit fault. Ensure electricity safety for non-faulty users. This product has the FTU function to realize the switch remote control opening and closing, and also has the GPRS remote control function.
1. Ambient air temperature: -5~+40 and the average temperature should not exceed +35 in 24h.2. Install and use indoors. Altitude above sea level for operation site should not exceed 2000M.3. Relative humidity should not exceed 50% at max temperature +40. Higher relative humidity is allowed at lower temperature. Ex. 90% at +20. But in view of the temperature change, it is possible that moderate dews will produce casually.4. Installation gradient not exceed 5.5. Install in the places without fierce vibration and shock and the sites insufficient to erode the electrical components.6. Any specific requirement, consult with manufactory.
A corner of the production workshop
Product application case